RIO head-end adaptor module Modicon Quantum - 1 connector with single cableShow more characteristics >
Main range of productModicon Quantum automation platform product or component typeRIO head-end adaptor module Complementary product compatibilityQuantum 200/500/800 seriesSymax (any mix) maximum drops/network31 I/O words/drop64 I/64 O type of cable75 Ohm coaxial cable transmission rate1544 Mbit/s dynamic range35 dB isolation voltage500 V DC coaxial center and ground electrical connection1 female connector F, elbowed with single cable diagnostics startupLAN controller checkMemory checkPower up power dissipation in W3 W 1 channel markingCE bus current requirement600 mA 1 channel module formatStandard Environment protective treatmentConformal coating Humiseal 1A33 product certificationsFM Class 1 Division 2 standardsCSA C22.2 No 142CULUL 508 resistance to electrostatic discharge4 kV contact conforming to IEC 801-28 kV on air conforming to IEC 801-2 resistance to electromagnetic fields10 V/m 80…1000 MHz conforming to IEC 801-3 ambient air temperature for operation0…60 °C ambient air temperature for storage-40…85 °C relative humidity95 % without condensation operating altitude<= 5000 m Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents & DownloadsLanguage
CatalogueSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsCLASS - C225351 - PROGRAMMABLE CONTROLLER,CLASS - C225802 - PROCESS CONTROL EQUIPMENT-For Hazardous Locations (Version 1.0)Declaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.