View all CT
contactor CT with manual control - 4 poles - 4 NO - 63 A - 220..240 V ACShow more characteristics
15988 has not been replaced. Please contact your customer care centre for more information.
The maximum number of products that can be compared is 4
Main product or component typeContactor device short nameCT device applicationControl circuit Poles4P [Ie] rated operational current63 A AC-7A pole contact composition4 NO network typeAC control typeRemote and manual control [Uc] control circuit voltage220/240 V AC 50 Hz Complementary network frequency50 Hz [Ue] rated operational voltage400 V AC 50 Hz maximum power13.8 W at 400 V AC control signal typeMaintained local signallingColor indicator hold-in power consumption in VA6.5 VA inrush power in VA53 VA mounting modeClip-on mounting support35 mm symmetrical DIN rail 9 mm pitches6 height81 mm width108 mm depth60 mm colourGrey mechanical durability1000000 cycles electrical durability100000 cycles IEC/EN 61095 63 A 50 Hz AC-7A30000 cycles IEC/EN 61095 50 Hz AC-7B30000 cycles IEC/EN 61095 50 Hz AC-7C100000 cycles EN/IEC 60947-4-1 50 Hz AC-130000 cycles EN/IEC 60947-4-1 50 Hz AC-330000 cycles EN/IEC 60947-4-1 50 Hz AC-5A connections - terminalsControl circuit: tunnel type terminals2 cable(s) 2.5 mm² flexibleControl circuit: tunnel type terminals2 cable(s) 1.5 mm² rigidPower circuit: tunnel type terminals2 cable(s) 10 mm² flexiblePower circuit: tunnel type terminals1 cable(s) 25 mm² rigid product compatibilityAuxiliary contactTime delayInterference filterMixed control: impulse/latched compatibility codeCT Environment standardsIEC/EN 61095 product certificationsEACCEBECCCCVDEIMQ noise level30 dB IP degree of protectionIP20 pollution degree2 tropicalisation2 conforming to EN 60947-4-12 conforming to EN 610952 conforming to IEC 1095 relative humidity95 % at 55 °C operating altitude2000 m ambient air temperature for operation-5…60 °C ambient air temperature for storage-40…60 °C Contractual warranty Warranty18 months
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.