View all Acti 9 iPRD
View all Acti 9 iPRD
PRD40r modular surge arrester - 3 poles - 460V - with remote transferShow more characteristics >
16563 has not been replaced. Please contact your customer care centre for more information.
Add to My Products Remove from My Products
Main range of productMulti 9 product nameMulti 9 PRD product or component typeSurge arrester with pluggable cartridge device short namePRD40r device applicationDistribution poles description3P remote signallingWith signal contacts composition1 SD (1 C/O) surge arrester typeElectrical distribution network earthing systemIT Complementary surge arrester class typeType 2 surge arrester technologyMOV [Ue] rated operational voltage230 V (+/- 10 %) AC 50/60 Hz [In] nominal discharge currentCommon mode : 15 kA L/PECommon mode : 15 kA N/PE [Imax] maximum discharge currentCommon mode : 40 kA L/PE [Uc] maximum continuous operating voltageCommon mode : 460 V L/PE [Up] voltage protection level<= 1.9 kV type 2 common mode L/PE [I total] discharge current120 kA disconnector device typeAssociated circuit breaker 40 A - Icu 10 kAAssociated circuit breaker 40 A - Icu 15 kAAssociated circuit breaker 40 A - Icu 25 kA signalling circuit voltage0.25 A/250 V AC 50/60 Hz mounting modeClip-on mounting supportDIN rail 9 mm pitches6 height81 mm width54 mm depth69 mm colourGrey ( RAL 7035 ) response time<= 25 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque2.5 N.m Environment quality labelsNFKEMA-KEUROVE IP degree of protectionOn front face : IP40 conforming to IEC 60529On terminal : IP20 conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Contractual warranty Warranty period18 months 18 months
Documents & DownloadsLanguage
Instruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.