Main product nameUA product or component typeControl unit Complementary [Us] rated supply voltage220...240 V AC at 50/60 Hz operating modeForced operation on replacement sourceStop (both normal and replacement source off)Automatic operationForced operation on normal source interlocked deviceMasterpact NWCompact NS100...630Compact NS630b...1600Masterpact NT selection modesCircuit breaker on RCircuit breaker on N genset exerciserStartup controlAdjustable delayed shutdown test functionBy pressing the test button on the front of the controller complementary functionSelection of type of normal source (single-phase or three-phase)Setting of maximum startup time for the replacement sourceVoluntary transfer to replacement source (e.g. energy management commands)Forced normal source if replacement source not operational during peak-tariffAdditional contact: transfer to replacement source only if contact is closed local signallingFault tripOnOff input typeContacts customer voluntary order to transfer to source R output typeContacts customer: indication of operation in automatic or stop mode [Ith] conventional free air thermal current8 A [Ie] rated operational currentAC-12: 4 A AC 440 VAC-12: 5 A AC 380/415 VDC-13: 2 A 24 V Environment standardsIEC 947-5-1 IP degree of protectionIP20 connectors: conforming to EN 60529IP40 front: conforming to EN 60529IP30 side: conforming to EN 60529 IK degree of protectionFront: IK07 conforming to EN 50102 Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsCatalogueFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.