Main ProductSurge protection device RangeSurgelogic Device Short NameHWA Complementary Surge Current100 kA per phase Voltage Rating120/240 V AC Number of Phases1 phase Wiring Configuration3-wire ConnectionWire phase and neutral AWG 10 copperWire ground AWG 10 copperWire dry contacts AWG 22 copper MCOV150 V Nominal Discharge Current20 kA Max Number of Poles1 SCCR200 kA Local SignallingStatus LED green per phase normal operationStatus LED red per phase faultAlarm fault Mounting LocationBack of enclosure Device MountingSurfaceFlush fixing kit Height4.80 in (122 mm) Width8.62 in (219 mm) Depth3.11 in (79 mm) Environment Enclosure RatingNEMA 4X Enclosure Materialblack plastic StandardsUL 1449:ed. 4CSA C22.2 No 8:1986UL 1283IEC 61643-1 Ambient Operating149 °F (65 °C) Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 2.9 MBDate 23/08/12DescriptionThis catalog covers Surgelogic models SDSB1175, SDSB1175CB, SDSB1175R,SDSB1175RB whole house surge protective devices and accessories, HEPD HEPD80 Home Electronics Protective Devices, and Square D brand QO and Homeline plug-on surge protective devices. Information included: selection tables, specifications, dimension drawings and wiring diagrams.CADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsSize pdfSize 4.4 MBDate 01/07/16DescriptionThis bulletin includes storage, electrical, grounding, installation, wiring, operation, and maintenance instructions for Surgelogic™ HWA SPDs.China RoHS declarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.