CatalogueLanguageFormatTailleDateGuide d'utilisationLanguageFormatTailleDatefrançaisprp.document.label.format pdfTaille 8.3 MBDate 19-10-01DescriptionCe document présente une fonctionnalité de PlantStruxure : l’horodatage système à la source.Ce guide fournit des informations détaillées sur l'horodatage système, notamment concernant lesaspects suivants :- Architecture de l'horodatage système- Phases de conception et de configuration- Phases de mise en service et d'exploitation- Interface avec un client SCADA tiersanglaisprp.document.label.format pdfTaille 7.8 MBDate 19-10-01DescriptionThis document presents a PlantStruxure feature: at source system time stamping. This guide presents detailed information about system time stamping, including the following:- System time stamping architecture- Design and configuration phases- Commissioning and operation phases- Interface with a 3rd party client SCADA interfaceanglaisprp.document.label.format zipTaille 866.8 KBDate 03-11-21Fichiers dans le documentDescriptionThis specification is an interface for developers of OPC clients and OPC Data access Servers. The specification is a result of an analysis and design process to develop a standard interface to facilitate the development of servers and clients by multiple vendors that shall inter-operate seamlessly together.
LogicielLanguageFormatTailleDateanglaisprp.document.label.format zipTaille 909.4 MBDate 16-01-07Fichiers dans le documentzip303.4 MBzip303 MBzip303 MBhtm73.4 KBDescriptionVersion contents : (see readme.html file) Note : The Small version software product gets the same features as the Large one but with the following restrictions : • Size of the application (Number of items managed by the server) limited to 1000 • OPC XML protocol and Web interface non available on this version The DEMO version software product gets the same features as the Large one but with the following restrictions : • Limited time of 3 days at each executionanglaisprp.document.label.format zipTaille 972.8 MBDate 13-12-06Fichiers dans le documenthtm172 Bzip324.1 MBhtm172 Bzip323.7 MBhtm172 Bzip323.7 MBhtm44.3 KBDescriptionVersion contents : Easier configuration and tuning Communication & tuning the Configuration have been made simpler by reducing number the number of communication parameters Moreover, Default configuration have been pretuned and optimized for Vijeo Citect environment Advanced PLC diagnostic information Deep and advanced diagnostic information for PSX PLCs is made available at SCADA level via specific items : more than 60 status variables are available for all or PLC platforms (Quantum, Premium, M340 and M580) For security reasons, these variables are accessible in Read Only Improved performances Application response time at SCADA level enhanced by giving high priority to write commands communication requests Overpassing Modbus communication capabilities by a new exclusive located data access mode. Miscellaneous Compatible with all main Windows platforms, 32 bits and 64 bits Windows 7, Windows 8, Windows 2008 terminal server. We deliver a new document named ‘Tuning the communication parameters’ explaining in a detailed way how to tune and optimize the PLC <>SCADA communications Note : The Small version software product gets the same features as the Large one but with the following restrictions : • Size of the application (Number of items managed by the server) limited to 1000 • OPC XML protocol and Web interface non available on this version The DEMO version software product gets the same features as the Large one but with the following restrictions : • Limited time of 3 days at each executionanglaisprp.document.label.format zipTaille 1.3 GBDate 13-01-29Fichiers dans le documenthtm171 Bzip686.2 MBhtm171 Bzip686.2 MBhtm98.8 KBzip1.6 MBDescriptionVersion contents: Time Stamping OFS V3.40 is able to manage at source time stamped digital data natively, transparently and with guaranty not to lose any data in case of burst of events. OFS V3.40 gets the time stamped data directly from the sources, which can be either BMX ERT module (1ms resolution) or any regular X80 digital remote IO (10ms resolution) behind X80 performance IO adapter, and push it to the SCADA via standard OPC DA protocol. OPC UA Compatibility OFS V3.40 brings also connectivity to OPC UA (Unified Architecture) clients via an OPC UA wrapper, intending to convert OPC DA protocol into OPC UA protocol. Note that OFS is getting at source time stamped data, then the data delivered to the OPC UA wrapper will be also at source time stamped. For information, OFS V3.40 also embeds : • A Time Stamping system guide • A tool to help evaluate response time in architectures with at source time stamping data (‘OFS Time Stamp Helper’) • All firmwares and Hot Fixes required in a time stamping architectures Note : The Small version software product gets the same features as the Large one but with the following restrictions : • Size of the application (Number of items managed by the server) limited to 1000 • OPC XML protocol and Web interface non available on this versionLogiciel - Mises à jourLanguageFormatTailleDateanglaisprp.document.label.format zipTaille 1.7 GBDate 19-05-06Fichiers dans le documenthtml4.4 KBzip437.2 MBzip436.8 MBzip436.8 MBzip437.3 MBDescriptionEnhancements - Bug Fixing : OFS 3.62 - 3303 SP1 Bug fixing : A crash may occur when IOPCAsyncIO2::Refresh is performed concurrently to IOPCItemMgt::RemoveItemsBug fixing : A hang may occur when activating items with IOPCItemMgt::SetActiveState or IOPCItemMgt::AddItems is performed concurrently to IOPCItemMgt::RemoveItems Bug fixing : A hang may occur on communication timeout when PLC link redundancy is configured. Bug fixing : The PLC link redundancy switch may be not performed if Address1 and Address 2 never got a common online status Bug fixing :On EcoStruxure Control Expert build change, Program Units items populated with XVM symbol link were discarded Bug fixing : Write operation on array of items postfixed with ";s" was badly performed if the item had not VT_UI1 type (for instance myAlias!%MW10:4;s) Bug fixing : Activation of a pending or missing license may fail. Bug fixing : The diagnostics window may not log new information after overflow was mitigated.Bug fixing : The Configuration tool Device Address Wizard did not show PL7, XTEL and ORPHEE PLC types. Bug fixing : A same item activated several times may miss an activation after a data dictionary update. Bug fixing : Unlocated items accessed with PRJ Concept link may fail.anglaisprp.document.label.format zipTaille 1.2 GBDate 17-07-20Fichiers dans le documenthtm61.1 KBzip318.4 MBzip318 MBzip317.9 MBzip310.8 MBDescriptionOPC Factory Server V3.60.3112 SP4Enhancements - Bug Fixing :Bug fixing : A crash may occur on TimeStamp Event Group deactivation when PLC link redundancy is configured.Bug fixing : The option Symbol Access Mode \ Located Only is no more supported.Bug fixing : Write operation used to fail on not array items or on array items of size 1 for which item requested type is VT_ARRAY.Bug fixing : Communication errors on XWAY/ Uni-Te V2 may lead in certain cases to unrecoverable communication break, particularly on high communication flow.Bug fixing : When “Quick Item Validation” is not configured, bad device access was not returned to IOPCItemMgt::ValidateItems() This Service Patch includes the previous ones (see content.htm file).anglaisprp.document.label.format zipTaille 1,013.2 MBDate 16-12-16Fichiers dans le documenthtm9 KBzip255.4 MBzip255 MBzip255 MBzip247.8 MBDescriptionOPC Factory Server V3.60.3111 SP3Enhancements - Bug Fixing : Bug fixing : In some cases of device access with burst of requests, the garbage collector was not able to stabilize memory consumption. Bug fixing : A memory leak occured when PLC link redundancy is configured. Bug fixing : When a connection is closed by the target device (gracefully or not), other open connections to the device might become unusable. This Service Patch includes the previous ones (see content.htm file).anglaisprp.document.label.format zipTaille 765.4 MBDate 16-08-01Fichiers dans le documenthtm8.5 KBzip255.4 MBzip255 MBzip255 MBDescriptionOPC Factory Server V3.60.3110 SP2Enhancements - Bug Fixing : Bug fixing : Active items may not access devices at the actual group update rate. OPC groups update rate is now revised (through IOPCServer::AddGroup or IOPCGroupStateMgt::SetState) to the nearest multiple of 50ms (for instance 420ms is revised to 400ms, 430ms to 450ms). Minimum supported update rate is 300ms (500ms for TimeStamp event group). Bug fixing : Unity data dictionnary loading may fail on Unity application modified without explicit build command. Bug fixing : A memory leak occured on Synchronous or Asynchronous Read operations. Bug fixing : #PLCQualStatus may not reflect the actual device connection status when used as a single active item on event sources, devices without alias or with alias with /Q or /NQ postfix. Bug fixing : #TSEventSynchro write operation could not be interrupted on a missing event source. It is now interrupted after a certain amount of retries. Bug fixing : PLC event sources configured with redundant addresses may be badly managed on TimeStamp Event Group activation\ deactivation sequences. Enhancement : #SwitchPrimaryAddress value and quality are updated as below : Read value 0: indicates that primary communication path is Device Address A. Read value 1: indicates that primary communication path is Device Address B. Read value 2: indicates that standby communication path is not configured (new feature) Quality QUAL_BAD : Communication with the device is interrupted, the primary, and standby communication paths are OFFLINE. Quality QUAL_UNCERTAIN : Communication with the device is correct but the standby communication path is OFFLINE (new feature) Quality QUAL_GOOD : Communication with the device is correct, the primary and standby communication paths are ONLINE