a in mm
a in in.
BMXXBP0400 and BMXXBP0400H
BMXXBP0600 and BMXXBP0600H
BMXXBP0800 and BMXXBP0800H
BMXXBP1200 and BMXXBP1200H
Main range of productModicon X80 product or component typePower supply module backplane compatibilityNot compatible with BMEXBP..02 primary voltage100...240 V supply circuit typeAC secondary power10.8 W 24 V DC sensor power supply16.8 W 24 V DC I/O module power supply and processor8.3 W 3.3 V DC I/O module logic power supply Complementary primary voltage limit85...264 V network frequency50/60 Hz network frequency limits47…63 Hz apparent power0.07 kVA input current0.31 A 240 V0.61 A 115 V inrush current30 A 120 V60 A 240 V I²t on activation12 A².s 240 V It on activation0.06 A.s 240 V0.03 A.s 120 V protection typeInternal fuse not accessible for primary circuitOverload protection for secondary circuitOvervoltage protection for secondary circuitShort-circuit protection for secondary circuit current at secondary voltage0.45 A 24 V DC sensor power supply0.7 A 24 V DC I/O module power supply and processor2.5 A 3.3 V DC I/O module logic power supply maximum power dissipation in W8.5 W status LED1 LED (green)rack voltage OK: 1 LED (green)sensor voltage: control typeRESET push-button cold restart electrical connection1 connector 2 pin(s)alarm relay1 connector 5 pin(s)line supply, protective earth, 24 V DC input sensor insulation resistance>= 100 MOhm primary/ground>= 100 MOhm primary/secondary net weight0.3 kg Environment immunity to microbreaks1 ms dielectric strength1500 V primary/secondary I/O module logic power supply1500 V primary/secondary I/O module power supply and processor2300 V primary/secondary sensor power supply1500 V primary/ground500 V 24 V sensor output/ground vibration resistance3 gn shock resistance30 gn IP degree of protectionIP20 directives2014/35/EU - low voltage directive2014/30/EU - electromagnetic compatibility2012/19/EU - WEEE directive product certificationsMerchant NavyCSAULCERCMEAC standardsEN 61131-2EN 61000-6-4EN 61000-6-2EN 61010-2-201 ambient air temperature for storage-40…85 °C ambient air temperature for operation0…60 °C relative humidity5…95 % at 55 °C without condensation protective treatmentTC operating altitude0...2000 m2000...5000 m with derating factor Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 12.3 MBDate 10/1/19DescriptionThis document provides detailed information about the M580 programmable automation controller (PAC), power supplies, and racks. These topics are also discussed:- Install a local rack in the M580 system.- Configure the M580 CPU.- The CPU performs Ethernet I/O scanning of both RIO and DIO logic without affecting network determinism.prp.document.label.format pdfSize 16.4 MBDate 10/1/19DescriptionThis document presents one of the PlantStruxure features, using Ethernet as the backbone around the Modicon M580 offer and connecting an M580 local rack and M580 RIO drops.This guide provides detailed information about the Modicon M580 Hot Standby system, in a simple daisy chain loop topology.prp.document.label.format pdfSize 12 MBDate 9/1/19DescriptionThis Safety Manual describes the modules of the M580 safety system with special regard as to how they meet the Safety requirements of the IEC 61508 standard. It provides detailed information on how to install, run, and maintain the system correctly in order to protect human beings as well as to prevent damage to environment, equipment, and production.prp.document.label.format pdfSize 7.9 MBDate 9/1/19DescriptionThis Safety System Planning Guide describes the modules of the M580 Safety system with special regard to how they meet the Safety requirements of the IEC 61508. It provides detailed information on how to install, run, and maintain the system correctly in order to help protect human beings as well as to help prevent damage to environment, equipment, and production.prp.document.label.format pdfSize 4.1 MBDate 12/1/18DescriptionThis manual presents, using a documented example, how to use motion function blocks (MFB) with Modicon M340 using EcoStruxure™ Control Expert. These blocks enable simplified management of servodrives and servo-amplifiers using the CANopen bus.prp.document.label.format pdfSize 868.1 KBDate 12/1/18DescriptionThis manual describes the hardware installation of PLCs in the Modicon M340 range as well as the installation of their main accessories. This document is also valid for the Modicon M340H PLCs and their accessories.prp.document.label.format pdfSize 3 MBDate 12/1/18DescriptionThis document provides detailed information about the Modicon X80 racks and power supplies used for M340 station, M580 system, and X80 drops.prp.document.label.format pdfSize 3.7 MBDate 12/1/18DescriptionThis document presents one of the PlantStruxure features, using Ethernet as the backbone around the Modicon M580 offer to facilitate communications between an M580 local rack and remote subrings through dual-ring switches (DRSs). This guide provides detailed information about planning complex M580 architectures, including these: - implementation of DRSs to support sub-rings - topology rules and recommendations for choosing a complex network configuration - system performance and limitations - system diagnosticsprp.document.label.format pdfSize 18.3 MBDate 12/1/18DescriptionThis document presents one of the PlantStruxure features, using Ethernet as the backbone around the Modicon M580 offer and connecting an M580 local rack and M580 RIO drops. This guide provides detailed information about planning frequently used M580 architectures, including the following: - Ethernet I/O networks (RIO and distributed equipment integrated on the same physical network) - topology rules and recommendations for choosing a network configuration - role of network option switch modules - system commissioning and maintenance - system performance and limitations - system diagnosticsprp.document.label.format pdfSize 1.8 MBDate 12/1/18DescriptionThis guide provides information about the Change Configuration on the Fly (CCOTF) feature in a M580 system, using Control Expert software.prp.document.label.format pdfSize 1.7 MBDate 12/1/18DescriptionThis document describes the adapter modules that can be used in X80 RIO drops. This guide describes 3 adapter modules: - BMECRA31210 - BMXCRA31210 - BMXCRA31200CADFormatSizeAdd to My DocumentsBrochureFormatSizeAdd to My Documentsprp.document.label.format zipSize 23.7 MBDate 3/15/18CertificateFormatSizeAdd to My Documentsprp.document.label.format zipSize 343.5 KBDate 12/17/19prp.document.label.format zipSize 2.2 MBDate 2/9/19prp.document.label.format pdfSize 92.9 KBDate 1/23/19DescriptionHazardous location Class I Division 2 by CSA for US and CanadaChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsMarine certificateFormatSizeAdd to My Documentsprp.document.label.format pdfSize 4.6 MBDate 2/18/19DescriptionClassNK Marine Certificate Modicon M340-M580prp.document.label.format pdfSize 181.4 KBDate 1/11/19DescriptionMerchant navies Installation Instructionsprp.document.label.format pdfSize 412.5 KBDate 1/7/19DescriptionBureau Veritas - marine certificate for QUANTUM PLCsprp.document.label.format pdfSize 3 MBDate 5/18/18DescriptionRussian Maritime Register of Shippingprp.document.label.format pdfSize 205 KBDate 5/18/18DescriptionDet Norske Veritas - Germanischer LloydProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages38
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsModules Mounted on RacksDimensions(1)With removable terminal block (cage, screw or spring).(2)With FCN connector.(3)On AM1 ED rail: 35 mm wide, 15 mm deep. Only possible with BMXXBP0400/0400H/0600/0600H/0800/0800H rack.
Connections and SchemaConnection of Alternating Current Power Supply ModulesConnection of a PLC Station Constituted of a Single RackQGeneral isolatorKMLine contactor or circuit breaker(1)Insulation connector bar for locating grounding errors(2)Available current of 0.45 A for the BMXCPS2000 module or 0.9 A for the BMXCPS3500 moduleConnection of a PLC Station Constituted of Several RacksQGeneral isolatorKMLine contactor or circuit breaker(1)Insulation connector bar for locating grounding errors(2)Available current of 0.45 A for the BMXCPS2000 module or 0.9 A for the BMXCPS3500 module