Main rangeTeSys product nameTeSys F product or component typeChangeover contactor device short nameLC2F contactor applicationResistive load utilisation categoryAC-1 device presentationPreassembled with reversing power busbar poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current275 A (at <40 °C) at <= 440 V AC AC-1 auxiliary contact composition1 NO [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current275 A (at 40 °C) Irms rated making capacity1850 A AC conforming to IEC 60947-4-1 rated breaking capacity1480 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current1500 A 40 °C - 10 s920 A 40 °C - 30 s740 A 40 °C - 1 min500 A 40 °C - 3 min400 A 40 °C - 10 min associated fuse rating200 A aM at <= 440 V315 A gG at <= 440 V average impedance0.33 mOhm - Ith 275 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole25 W AC-1 interlocking typeMechanical mounting supportPlate standardsIEC 60947-4-1JIS C8201-4-1EN 60947-1EN 60947-4-1IEC 60947-1 product certificationsABSRINARMRoSCSAULCCCLROS (Lloyds register of shipping)CBDNV connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bar 2 cable(s) - busbar cross section: 25 x 3 mmPower circuit: connector 1 cable(s) 150 mm²Power circuit: lugs-ring terminals 1 cable(s) 150 mm² tightening torqueControl circuit: 1.2 N.mPower circuit: 18 N.m Environment IP degree of protectionIP2x front face with shrouds conforming to IEC 60529IP2x front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C operating altitude3000 m without derating fire resistance850 °C conforming to IEC 60695-2-1 mechanical robustnessVibrations contactor open: 2 Gn, 5...300 HzShocks contactor closed: 15 Gn for 11 msVibrations contactor closed: 5 Gn, 5...300 HzShocks contactor open: 7 Gn for 11 ms height174 mm width437 mm depth181 mm net weight12.1 kg Packing Units Package 1 Weight13.240 kg Package 1 Height3.200 dm Package 1 width3.100 dm Package 1 Length5.000 dm Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins PVC freeYes Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My Documentsprp.document.label.format pdfSize 118.2 MBDate 7/22/20DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...). This edition includes a presentation of the new TeSys island system. The catalogue can also be downloaded chapter per chapter.CertificateFormatSizeDateAdd to My DocumentsInstruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My DocumentsEnd of Life InformationFormatSizeDateAdd to My DocumentsEU RoHS DeclarationFormatSizeDateAdd to My DocumentsProduct Environmental ProfileFormatSizeDateAdd to My Documents
- All Languages12
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.