Sepam serie 80
Protection relays for custom applications
16 types of digital curent or voltage protection for any distribution system, each one dedicated to a single application: Easergy Sepam S80, S81, S82, S84, T81, T82, T87, M81, M87, G88, B80, B83, C86. A ready to use Easergy Sepam includes: one base unit, two 20 pin connectors, one current, one current and one voltage connector, one memory cartridge, one application, one language, logipam firmware option, TCP/IP option, optional modules, comm. interfaces or core balance CT.
Software - ReleasedLanguageFormatSizeDateEnglishprp.document.label.format exeSize 119 MBDate 12/15/19DescriptionCET850 is the IEC 61850 Edition 1 & 2 configurator associated with the Sepam/Easergy P3 and P5 /ION7x50/ION8650/MTZ devices.The CET850 software enables protection and integration engineers to designautomated substations containing Schneider Electric Intelligent Electronic Devices(IED) compliant with the IEC 61850 Standard.CET850 provides a set of functions to create, edit, and display IEC 61850configuration files based on the Substation Configuration Language (SCL)in conformance with IEC 61850 part 6.CET850 deals with the following SCL files:- ICD files: IED Capabilities Description- IID files: Instantiated IED Description- CID files: Configured IED Description- SCD files: Substation Configuration DescriptionCET850 is delivered with a library of ICD files that provides the IEC 61850 descriptionof the Schneider Electric Sepam,ION7x50,ION8650 and G3200 range IEDs.CET850 can be used to:- Create an IEC 61850 configuration or modifying an existing one by adding Sepam IEDs using their ICD file.- Edit an SCL file (ICD, IID, CID or SCD) to modify its contents: > Display the device and system configuration > Add or remove IEDs > Set or modify the communication parameter values > Optimize the configuration by creating or modifying Datasets, Report Control Blocks and Goose Control Blocks.- Generate the CID file for storing the configuration of one IED, which can then be downloaded to the devices via FTP protocol , or SFT2841 Sepam commisionning tool for SEPAMs only.- Generate an IID file for storing the configuration of an IED which can then be used by other IEC 61850 configuration tools.- Generate an SCD file for storing the configuration of an IEC 61850 system which can then be used by other IEC 61850 configuration tools.CET850 enables the optimization of data transfered within the system by:- Creating or adapt DataSets to gather relevant data- Creating or adapt Report Control Blocks to define the transmission conditions- Setting deadband values for sending measurements reports- Creating or adapt Goose Control Blocks to define the peer-to-peer data exchange based on the producer/consumer communication model.The configuration of peer-to-peer communication between Sepam devices (Goose messaging)is avalaible to implement specific distributed protection and control functionslike inter-locking, inter-tripping, logic discrimination, ... CET850 is delivered with a library ICD files for all devices range IEDs.ICD files from other manufacturers may be used, and IID, SCD and CID files coming from otherIEC 61850 configuration tools may be edited with CET850.Nevertheless, some specific editing features are restricted to Schneider Electric IEDs.Englishprp.document.label.format pdfSize 72.5 KBDate 5/10/07Description"The Sepam firmware update is a delicate operation. If this update is not done properly, the Sepam may be out of order.In order to avoid inappropriate updates, the Sepam patch which has been developed to fix a technical problem by updating the Sepam will be encoded with the Sepam Serial Number. This will guarantee a proper update on a batch of Sepams. The patch would have been tested for the Sepams which it will update.PMC wants to guarantee the customers a proper Sepam update and ensures them a steady hand during the update. Please find enclosed the process to receive Sepam updates."