Main range of productActi 9 product or component typeOC and fault contact device short nameOF and SD signal contacts composition2 C/O [In] rated current3 A: 415 V AC - 50/60 Hz6 A: <= 240 V AC - 50/60 Hz1 A: 130 V DC3 A: <= 48 V DC 9 mm pitches1 Complementary range compatibilityActi 9 NG125NAActi 9 NG125LMAActi 9 NG125 [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to EN/IEC 60947-5-1 [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-5-1 mounting modeFixed mounting supportDIN rail height102.8 mm width15.3 mm depth75.5 mm electrical durability10000 cycles conforming to EN/IEC 60947-5-1 connections - terminalsPlate terminal1 cable(s) 0.5…2.5 mm² - rigidPlate terminal1 cable(s) 0.5…1.5 mm² - flexiblePlate terminal1 cable(s) 0.5…1.5 mm² - flexible with ferrulePlate terminal2 cable(s) 2.5 mm² - rigidPlate terminal2 cable(s) 2.5 mm² - flexiblePlate terminal2 cable(s) 1.5 mm² - flexible with ferrule wire stripping length10 mm tightening torque1 N.m Environment standardsEN/IEC 60947-5-1 product certificationsLCIEKEMAASEFAASTA pollution degree3 conforming to EN/IEC 60947-5-1 tropicalisation2 conforming to EN/IEC 60947-5-1 ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.