Main device short nameMN product or component typeVoltage release device applicationControl range compatibilityMasterpact NW voltage release typeUndervoltage release [Uc] control circuit voltage380...480 V AC Complementary threshold tripping voltage0.35...0.7 Un - during opening time0.85 Un - during closing time supply holding power4.5 VA mounting modeDrawout response time90 ms Masterpact NW Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.