Main rangeCanalis product nameKT product or component typeElbow busbar descriptionStandard device short nameKTA device applicationChange direction materialAluminium [Ie] rated operational current2500 A at 35 °C busbar trunking polarity3L + N + PER direction change typeDirection 1 : flat to right operating angle90 ° earth circuitReinforced variantReinforced version provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current113 kA [Ipk] rated peak withstand current248 kA radiated magnetic field1.6 µT thermal stress limit12769 A².s THDI0...15 %, maximum load current: 2500 A15...33 %, maximum load current: 3200 A33...100 %, maximum load current: 4000 A voltage dropWith cos φ =1, 0.0024 V at 50 Hz with 1A for 100 m longWith cos φ =0.9, 0.0025 V at 50 Hz with 1A for 100 m longWith cos φ =0.8, 0.0024 V at 50 Hz with 1A for 100 m longWith cos φ =0.7, 0.0022 V at 50 Hz with 1A for 100 m long standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure width140 mm height244 mm lengthDirection 1 : 300 mmDirection 2 : 800...1100 mm colourGrey : RAL 7035 linear load36 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 ambient air temperature for operation100 % of In at 0...35 °C
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.