Main range of productCanalis product nameKS product or component typeBusbar trunking busbar descriptionDistribution length BAR MATERIALAluminium device applicationMedium power distribution [Ie] rated operational current250 A at 35 °C number of tap-off outlets12 Complementary [Ue] rated operational voltage230...690 V network frequency50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ui] rated insulation voltage690 V [Icw] rated short-time withstand current10 kA [Ipk] rated peak withstand current28 kA electrical connectionLubricated sliding contact radiated magnetic field0.69 µT thermal stress limit100 kA².s THDI0…15 % 250 A15…33 % 200 A33…100 % 160 A maximum voltage drop<0.034 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.036 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.035 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.034 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy screws mounting positionHorizontal neutral positionUp busbar trunking polarity3L + N + PE3L + PEN dimension typeFix width146 mm depth54 mm length3 m net weight14.6 kg Environment standardsIEC 61439-6IEC 60439-2 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages10
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.