Main rangeCompact range of productNSX400...630 product or component typeBasic frame device short nameCompact NSX400L device applicationDistribution circuit breaker nameCompact NSX400L poles description4P neutral positionLeft network typeAC network frequency50/60 Hz [In] rated current400 A at 40 °C [Ui] rated insulation voltage800 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-2 breaking capacity codeL breaking capacity130 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-2150 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-2150 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 525 V AC 50/60 Hz conforming to IEC 60947-270 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity130 kA at 440 V AC 50/60 Hz conforming to IEC 60947-2150 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-2150 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-270 kA at 500 V AC 50/60 Hz conforming to IEC 60947-212 kA at 525 V AC 50/60 Hz conforming to IEC 60947-212 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-2 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A pollution degree3 conforming to IEC 60947-1 Complementary control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront protection typeWithout protection mechanical durability15000 cycles conforming to IEC 60947-2 electrical durability12000 cycles 440 V AC 50/60 Hz In/2 conforming to IEC 60947-23000 cycles 690 V AC 50/60 Hz In conforming to IEC 60947-26000 cycles 440 V AC 50/60 Hz In conforming to IEC 60947-26000 cycles 690 V AC 50/60 Hz In/2 conforming to IEC 60947-2 connection pitch45 mm height255 mm width185 mm depth110 mm Environment standardsUL 508IEC 60947-2EN 60947-2 product certificationsCSAUL IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 ambient air temperature for operation-35…70 °C ambient air temperature for storage-55…85 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight6.029 kg Package 1 Height15.5 cm Package 1 width20 cm Package 1 Length30 cm Unit Type of Package 2S04 Number of Units in Package 23 Package 2 Weight18.853 kg Package 2 Height30 cm Package 2 width40 cm Package 2 Length60 cm Unit Type of Package 3P12 Number of Units in Package 328 Package 3 Weight180.812 kg Package 3 Height62.5 cm Package 3 width80 cm Package 3 Length120 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 1.6 MBDate 01/04/20DescriptionThis document provides information about the backward compatibility between Enerlin’X devices and - MicroLogic control units for MasterPact MTZ circuit breakers- MicroLogic trip units for MasterPact NT/NW, ComPact NS630b-3200 and PowerPact P- and R-frame circuit breakers - MicroLogic trip units for ComPact NSX and PowerPact H-, J-, and L-frame circuit breakersprp.document.label.format pdfSize 5.7 MBDate 01/01/20DescriptionCompact NSX - Micrologic 5/6/7 - User guideCADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.