Main rangePowerLogic product nameCT product or component typeCurrent transformer secondary current5 A accuracy classClass 0.5 at 14.5 VAClass 1 at 21.5 VAClass 3 at 26 VA [In] rated current600 A Complementary current transformer typeTropicalised for busbar and cable current transformer ratio600/5 [Ith] conventional free air thermal current36 kA dynamic withstand current2.5 Ith maximum safety factor5 [Ue] rated operational voltage< 720 V AC 50/60 Hz [Ui] rated insulation voltage3 kV mounting modeBy screwsClip-onInsulated locking screw mounting supportMounting plateDIN railBusbar width56 mm outside: height84 mm outside: depth42 mm outside: diameter22 mm net weight0.34 kg [Uimp] rated impulse withstand voltage3 kV electrical insulation classClass B cable outer diameter22 mm opening of bars30.5 x 10.525.5 x 11.520.5 x 12.5 sealingWithout Environment standardsVDE 0414IEC 61869-2 product certificationsCE IP degree of protectionIP20 relative humidity0…95 % ambient air temperature for operation-25…60 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight356 g Package 1 Height7.2 cm Package 1 width7.2 cm Package 1 Length9.1 cm Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 12.3 MBDate 25/01/20DescriptionNote that no printed catalogs are available but all necessary source files, in 13 sections, are available for download from the Shopping Kiosk.CADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.