Main rangePowerLogic product nameCT product or component typeCurrent transformer secondary current5 A accuracy classClass 0.5 at 4 VAClass 1 at 8 VAClass 3 at 12 VA [In] rated current300 A Complementary current transformer typeTropicalised for busbar and cable current transformer ratio300/5 [Ith] conventional free air thermal current18 kA dynamic withstand current2.5 Ith maximum safety factor5 [Ue] rated operational voltage< 720 V AC 50/60 Hz [Ui] rated insulation voltage3 kV mounting modeBy screwsClip-onInsulated locking screw mounting supportMounting plateDIN railBusbar width77 mm outside: 40.5 mm inner: height107 mm outside: 40.5 mm inner: depth46 mm outside: diameter35 mm net weight0.429 kg [Uimp] rated impulse withstand voltage3 kV electrical insulation classClass B cable outer diameter35 mm opening of bars40.5 x 10.510.5 x 40.5 sealingWithout Environment standardsVDE 0414IEC 61869-2 product certificationsCE IP degree of protectionIP20 relative humidity0…95 % ambient air temperature for operation-25…60 °C Packing Units Package 1 Weight0.439 kg Package 1 Height0.700 dm Package 1 width0.900 dm Package 1 Length1.150 dm Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 12.3 MBDate 25/01/20DescriptionNote that no printed catalogs are available but all necessary source files, in 13 sections, are available for download from the Shopping Kiosk.CADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.