Main rangePragma product or component typeEnclosure enclosure typeDistribution enclosure width336 mm height450 mm depth123 mm Nb of 18 mm modules per row13 Nb of horizontal rows2 electrical insulation classClass IIDouble insulation provided equipment1 x identification label1 x marking kit1 x blanking plate strip3 x terminal block Complementary enclosure mountingSurface 9 mm pitches26 total number of 18 mm modules26 power dissipation in W40 W [In] rated current63 A type of railDIN cable entryTrunkingRemovable platesCable or tubeCut-out plates comb busbar and distribution block compatibilityXE compatible number of terminal blocks2 phase / neutral (Quick) with 7 outgoers1 earth (Quick) with 24 outgoers distribution block outgoers3 x 25 mm² for earth21 x 4 mm² for earth2 x 35 mm² for phase / neutral12 x 16 mm² for phase / neutral enclosure materialBack part: technoplasticFront face: technoplastic colourEnclosure: white (RAL 9016)Front face: white (RAL 9016) targeted countryFrance Environment fire resistanceBack part: 750 °CFront face: 750 °C IP degree of protectionIP30 without doorIP40 with door IK degree of protectionIK08 without doorIK09 with door overvoltage categoryII ambient air temperature for operation-25…60 °C standardsIEC 60670-1IEC 60670-24IEC 61439-1IEC 61439-3 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.