Differential Protection Devices for Complete Protection of Electrical Power Transformers
MiCOM P63x series differential protection devices are designed for fast, selective, short-circuit protection of transformers, motors, generators and other installations. Models available: MiCOM P630C, MiCOM P631, MiCOM P632, MiCOM P633, MiCOM P634
MiCOM P63x provides quick and selective differential protection. MiCOM 63x is easily interfaced to almost any kind of substation control or SCADA system. It is user-friendly and provides clear readings from extensive recordings.
High-speed, three-system differential protection
MiCOM P63x provides high-speed three-system differential protection using a triple-slope characteristic and two high-set differential elements in combination with transformer inrush restraint, overfluxing restraint and through-stabilization.
By entering the nominal values of transformer windings and associated CTs, users obtain amplitude and vector group matching. The devices also incorporate many supplementary protective functions. MiCOM P63x provides four setting groups for easy adaptation to varying system operation conditions.
Systems versatility and easy, clear readings
Equipped with 1A/5A setting software, MiCOM P63x has two communication interfaces for SCADA and RTU, and numerous communication protocols. It allows easy and complete device settings and readings from extensive recordings. Available for flush or wall mounting, MiCOM P63x benefits from InterMiCOM interfacing for direct end-end communication between two protection devices.
Standard Manufacturers Warranty: 2 years
EcoStruxure™ for Your BusinessEcoStruxure lets you thrive in today's digital world. Make better business decisions with scalable and converged IT/OT solutions. Learn more
Reach UsHave a question, complaint or is there some feedback you’d like to send us to make your experience with Schneider Electric better? Contact an Expert
Frequently Asked QuestionsEasily find and share the answer you are looking for from our online FAQ service Browse FAQ