Main product or component typeAdd-on residual current devices device short nameVigi NG125 poles description4P [In] rated current125 A network typeAC earth-leakage sensitivity300 mA1000 mA500 mA3000 mA earth-leakage protection time delayAdjustable instantaneous/selective/delayed earth-leakage protection classType A quality labelsNF Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage230...415 V AC 50/60 Hz residual current tripping technologyVoltage independent [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 mounting modeFixed mounting support35 mm symmetrical DIN rail electrical connection to mcbBy screws 9 mm pitches11 height118 mm width207 mm depth81 mm net weight0.8 kg connections - terminalsTunnel type terminals 10…50 mm² flexibleTunnel type terminals 16…70 mm² rigid wire stripping length20 mm tightening torque6 N.m Environment standardsIEC 60947-2 IP degree of protectionIP20 conforming to IEC 60947-2 pollution degree3 conforming to IEC 60947-2 electromagnetic compatibility8/20 µs impulse withstand, 5000 A conforming to IEC 60947-2 ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.