Main range of productEasypact CVS100...250 product or component typeCircuit breaker device short nameCVS100B device applicationDistribution poles description3P protected poles description3d Earth leakage protection (Vigi add on)Without breaking capacity codeB network typeAC [Icu] Breaking capacity40 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit rating63 A at 40 °C protection typeOverload protection (thermal)Short-circuit protection (magnetic) Complementary network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-2 [Ics] rated service breaking capacity15 kA at 440 V AC 50/60 Hz conforming to IEC 60947-225 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-240 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 mechanical durability30000 cycles electrical durability12000 cycles 415 V In conforming to IEC 60947-2 connection pitch35 mm contact position indicatorYes long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed short-time delay adjustment typeFixed instantaneous pick-up adjustment type IiFixed instantaneous pick-up adjustment range500 A height161 mm width105 mm depth86 mm Environment electrical shock protection classClass II standardsIEC 60947-2EN 60947-2 product certificationsGOSTIEC ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Offer Sustainability EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.