KatalogLanguageFormatStorlekDatumAnvändarmanualLanguageFormatStorlekDatumengelskaprp.document.label.format pdfStorlek 1 MBDatum 2019-12-04BeskrivningThis guide provides recommendations to better secure your Com’X device.Please use this guide in conjunction with the user manual for the step by step procedure details required for the configuration of specific features and settings.NOTE: This guide is applicable for Com'X firmware version 6.5 and above.
Firmware - ReleasedLanguageFormatStorlekDatumengelskaprp.document.label.format zipStorlek 47.9 MBDatum 2020-04-29BeskrivningIf your Com’X 210 device is currently running a firmware version earlier than v2.1, please upgrade to v2.1 before upgrading to later versions. This version (v6.6.5) contains cybersecurity updates. Please ensure you are using the most up-to-date version of your device’s firmware in order to access the latest features.engelskaprp.document.label.format zipStorlek 55.3 MBDatum 2020-04-29BeskrivningIf your Com’X 510 device currently runs a firmware version earlier than v2.1, please upgrade to v2.1 before upgrading to later versions. This release (v6.6.5) contains cybersecurity updates. Please ensure you are using the most up-to-date version of your device’s firmware in order to access the latest features.engelskaprp.document.label.format zipStorlek 39.3 MBDatum 2019-07-30BeskrivningIf your Com’X 200 device is currently connected to Digital Services Platform (DSP) in support of a cloud application such as EcoStruxure™ Facility Expert, it must be upgraded to firmware version v3.5.54 by August 1, 2019 to avoid interruption of service. After August 1, 2019 firmware versions v3.5.54 or later are required to connect to cloud applications via DSP.NOTE: Remote Access feature has been restored and functions as expected in Com’X v3.5.54. This release is the same as v3.5.53 with the Remote Access defect fixed.engelskaprp.document.label.format zipStorlek 115.8 MBDatum 2016-01-29Filer i dokumentzip40.2 MBbz275.5 MB139.3 KBBeskrivningCom’X 200/210 firmware updates: 1. After upgrading to V2.1.18 from a previous version, the Com’X occasionally fails to communicate to configured Zigbee devices on its first startup. To correct this, cycle the power to the Com’X orpress “Restart” on the Maintenance > System Settings page. This is not a reoccurring issue. 2. After upgrading to V2.1.18 from a previous version, measurements selected for publication arecleared. To continue to publish, the measurement selections must be reselected. Corrections: 1. Corrected issue where after an upgrade to V2.1.17, the Local IDs defaulted to 1, causing loss ofcommunications to devices. 2. Corrected issue where after an upgrade to V2.1.17, changing Local IDs in the Settings > ModbusGateway > Device IDs page caused the device to be removed or communications lost. Com’X 510 Corrections: 1. Corrected the issue of excessive time to load the Measurement Table for the CM4000 and CM3000 variants, which also reduced the gateway bandwidth. 2. Corrected issue where the data series in the 4 Weeks over 4 Weeks energy dashboard reportsinaccurate Date/Time values when the time zone is configured with a positive offset. 3. Updated the on-board User Manual to the correct 2.1 version.