Main product or component typeAdd-on residual current devices device short nameVigi NG125 poles description2P [In] rated current63 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType AC Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage230...415 V AC 50/60 Hz residual current tripping technologyVoltage independent [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 mounting support35 mm symmetrical DIN rail electrical connection to mcbBy screws 9 mm pitches5 height118 mm width99 mm depth81 mm net weight0.25 kg electrical durability10000 cycles conforming to IEC 60947-2 connections - terminalsTunnel type terminals 1…35 mm² flexibleTunnel type terminals 1.5…50 mm² rigid wire stripping length20 mm tightening torque3.5 N.m Environment standardsIEC 60947-2 IP degree of protectionIP40 conforming to IEC 60947-2 pollution degree3 conforming to IEC 60947-2 electromagnetic compatibility8/20 µs impulse withstand, 3000 A conforming to IEC 60947-2 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % at 55 °C operating altitude2000 m Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.