trip unit TM250D, Compact NSX 250, thermal magnetic, distribution protection, 250 A rating, 4P 4dShow more characteristics >
Main range of productNSX100...250 product or component typeTrip unit range compatibilityCompact NSX250 device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeAC network frequency50/60 Hz trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating250 A at 40 °C Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz neutral protection setting1 x Ir (4t) long time pick-up adjustment type IrAdjustable [Ir] long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120…400 s at 1.5 x In15 s at 6 x Ir short-time pick-up adjustment type IsdAdjustable [Isd] short-time pick-up adjustment range5...10 x In short-time delay adjustment typeFixed Environment standardsEN/IEC 60947-2UL 508 product certificationsCCCMarineEAC ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for LV431450: 4P3D TM TRIP UNIT FOR NSX100-250 CIRCUIT (Version 1.0)Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.