Main range of productActi 9 product or component typeUndervoltage release device short nameMNx [Uc] control circuit voltage220...240 V AC 50/60 Hz control typeStandard 9 mm pitches9 Complementary range compatibilityVigi NG125Acti 9 NG125LMAActi 9 NG125NAActi 9 NG125 [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to EN/IEC 60947-5-1 [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-5-1 local signallingAction indicator mounting modeFixed mounting support35 mm symmetrical DIN rail height109 mm width78 mm depth55 mm net weight0.199 kg electrical durability10000 cycles conforming to EN/IEC 60947-5-1 connections - terminalsPlate terminal - 1 cable(s) 0.5…2.5 mm² - rigidPlate terminal - 1 cable(s) 0.5…1.5 mm² - flexiblePlate terminal - 1 cable(s) 0.5…1.5 mm² - flexible with ferrulePlate terminal - 2 cable(s) 2.5 mm² - flexiblePlate terminal - 2 cable(s) 2.5 mm² - rigidPlate terminal - 2 cable(s) 1.5 mm² - flexible with ferrule wire stripping length10 mm tightening torque1 N.m Environment standardsEN/IEC 60947-5-1 product certificationsASEFAKEMALCIEASTA IP degree of protectionIP20 B conforming to EN/IEC 60947-5-1IP4 conforming to EN/IEC 60947-5-1 pollution degree3 conforming to EN/IEC 60947-5-1 overvoltage categoryII tropicalisation2 conforming to EN/IEC 60947-5-1 relative humidity95 % at 55 °C ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveUnder investigation Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
User guideSizeAdd to My DocumentsCADSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.