Main rangeActi 9 product nameIKQ product or component typeCircuit breaker poles description1P number of protected poles1 [In] rated current10 A network typeAC trip unit technologyThermal-magnetic curve codeB breaking capacity10000 A Icn at 240 V AC 50/60 Hz conforming to EN 60898-1 Complementary network frequency50/60 Hz [Ue] rated operational voltage240 V AC 50/60 Hz magnetic tripping limit3...5 x In [Ics] rated service breaking capacity7500 A conforming to EN 60898-1 - 240 V AC 50/60 Hz limitation class3 conforming to EN/IEC 60898-1 [Ui] rated insulation voltage440 V AC 50/60 Hz conforming to EN/IEC 60898-1 [Uimp] rated impulse withstand voltage4 kV conforming to EN/IEC 60898-1 contact position indicatorYes control typeToggle local signallingTrip indicator mounting modePlug-on mounting supportRail 9 mm pitches2 height85 mm width18 mm depth78.5 mm net weight0.121 kg colourWhite mechanical durability20000 cycles electrical durability10000 cycles connections - terminalsSingle terminal (bottom) 1…25 mm² rigidSingle terminal (bottom) 1…16 mm² flexible wire stripping length14 mm for bottom connection tightening torque2 N.m bottom earth-leakage protectionWithout Environment standardsEN/IEC 60898-1 IP degree of protectionIP20 conforming to IEC 60529 pollution degree2 conforming to EN/IEC 60898-1 overvoltage categoryIII Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.