View all PowerPact B-Frame Molded Case Circuit Breakers
adjustable time delay relay for voltage release MN, 200-250 VAC 50/60 Hz, 200-250 VDCShow more characteristics
3368233682 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main device short nameMN delay unit product or component typeTime delay auxiliary device applicationControl range compatibilityMasterpact NTMasterpact NWCompact NSXCompact NS630b...1600Compact NS1600b...3200PowerPact Multistandard offer typeC5C4 voltage release typeInstantaneous [Uc] control circuit voltage200...250 V AC 50/60 Hz200...250 V DC Complementary impulse duration200 ms time delay range0.5...3 s threshold tripping voltage0.35...0.7 Un open 0.85 Un close supply holding power4.5 VA supply inrush power200 VA response time0.5 s0.9 s1.5 s3 s accessory / separate part categorySpare part Compact NS630b...1600Spare part Compact NS1600b...3200 Ordering and shipping details Category01081 - INTRA-COMPANY COMPONENTS Discount ScheduleNET GTIN03303430336822 ReturnabilityNo Country of originFR Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.