View all Compact NSF/NSJ
trip unit - STR53UP FTI - 3 poles 3dShow more characteristics
3694536945 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main range of productNSJ400...600 product or component typeTrip unit range compatibilityCompact NSJ400...600 device applicationDistribution poles description3P protected poles description3t network typeAC network frequency50/60 Hz trip unit nameSTR53UP trip unit technologyElectronic protection typeOverload protection (long time)Short time short-circuit protectionInstantaneous short-circuit protection trip unit rating250 A 104 °F (40 °C)400 A 104 °F (40 °C)630 A 104 °F (40 °C)150 A 104 °F (40 °C) earth-leakage protectionWith Complementary neutral protection setting0.5 x Ir1 x IrNo protection long time pick-up adjustment type IrAdjustable 8 settings [Ir] long time pick-up adjustment range0.8...1 x In long time delay adjustment typeAdjustable [tr] long-time delay adjustment range0.5…8 s short-time pick-up adjustment type IsdAdjustable 7 settings [Isd] short-time pick-up adjustment range1.5...7 x Ir short-time delay adjustment typeAdjustable 4 settings [tsd] short-time delay adjustment range0.015…0.06 s0.06…0.14 s0.14…0.23 s0.23…0.35 s instantaneous pick-up adjustment type IiAdjustable 7 settings ground-fault pick-up adjustment typeAdjustable 8 settings [Ig] ground-fault pick-up adjustment range0.2...1 x In ground-fault time delay adjustment type -tgAdjustable 4 settings display typeLED Environment product certificationsKEMAASTALCIE Ordering and shipping details Category01103-H,J,COMPACT NS UL/IEC CB ACCESS Discount ScheduleDE2 GTIN03303430369455 Package weight(Lbs)0.55 lb(US) (0.248 kg) ReturnabilityNo Country of originFR Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My Documents
- All Languages2
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.