View all NEMA Circuit Breaker Combination Starters
Non-Rever. Combo Starter Size 1, 3P, Motor Logic SSOLR, NEMA 12 +OptionsShow more characteristics
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main ProductCombination Starter TypeS Control Circuit TypeControl circuit transformer Complementary Control Circuit Voltage120 V AC 60 Hz secondary circuit480 V AC 60 Hz primary circuit Starter TypeNon reversing Number of Poles3P Horsepower Rating0.25…5 hp 200 V AC, 3 phase0.25…7.5 hp 230 V AC, 3 phase0.25…10 hp 460 V AC, 3 phase0.25…10 hp 575 V AC, 3 phase Maximum Voltage Rating600 V AC Control UnitsNo control units Pilot LightNo indicator Auxiliary Contacts1 NO + 1 NC Control Circuit Fusing2 fuses primary circuit1 fuse secondary circuit thermal overload typeSolid state Motor Logic class 10/20 3…9 A Disconnect TypeCircuit breaker, 30 A circuit breaker typeEMCP breaking capacity100 kA 480 V AC35 kA 600 V AC height24 in (609.60 mm) depth9.84 in (249.94 mm) width9.5 in (241.30 mm) Handle Swing3.25 in (82.55 mm) Environment Enclosure TypeNEMA 12 painted sheet steel with external reset NEMA size1 product certificationsUL listed file E152395 CCN NKJHCSA file 584 class 3211 04UL listed file E152395 CCN NKJH7 Ordering and shipping details Category21213 - 8538,39 SC,SD(NOT S*R,T,W) Discount ScheduleCP1 ReturnabilityYes Country of originMX Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause Carcinogen & Reproductive harm. For more information go to www.p65warnings.ca.gov EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
CertificateFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.