View all All-in-Ones
ALL-IN-ONE RING OH/UG 200ASURFACE VAL PKShow more characteristics
CSEDVP1CSEDVP1 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main product or component typeAll-In-One range of productQO meter socket typeRinged hub typeA-L Included OptionsCircuit breaker 1) 2P 200 A 120/240 V AC main supply ready assembledCircuit breaker 1) 2P 50 A 120 V ACCircuit breaker 2) 1P 15 A 120 V ACCircuit breaker 5) 1P 20 A 120 V AC Complementary Line Rated Current200 A short-circuit current22 kA MountingSurface number of spaces30 number of circuits40 Number of Tandem Breakers10 electrical connectionLugs line sideLugs service ground Wire SizeAWG 8...AWG 2/0 aluminium/copper)service groundAWG 4...250 kcmil aluminium/copper)line side DisconnectService disconnect (factory installed) Disconnect Rating200 A Branch Breaker Rating200 A service feed locationUGOH outdoor bypass typeNo bypass Ordering and shipping details Category01326 - HOME LINE ACCES. Discount ScheduleCPQ GTIN00785901884088 Package weight(Lbs)27.32 kg (60.23 lb(US)) ReturnabilityNo Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause cancer and birth defects or other reproductive harm.For more information go to www.p65warnings.ca.gov EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
CertificateFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.