View all Enerlin'X Com'X
ComX 210 - data logger - ULShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangePowerLogic product nameComX product or component typeEnergy server device short nameComX 210 Complementary [Us] rated supply voltageMain supply 24 V DC maximum power consumption in W26 W 24 V15 W via PoE communication network typeRS485, Modbus serial 1 RJ45RS485, Modbus serial terminal blockEthernet, PoE 15W (Power over Ethernet) 1 RJ45Ethernet, DHCP 1 RJ45 number of inputs6 digital2 analog discrete input current60 mA 12 V DC sensor power supply24 V DC 50 mA analogue input type4...20 mAPt 100Pt 10000...10 V communication gatewayEthernet TCP/IP to Modbus memory capacity128 MB RAM256 MB flash mounting modeClip-on mounting support35 mm DIN rail product certificationsCECULC-TickUL standardsEN 61010-1UL 508EN 60950UL 60950 depth2.72 in (69 mm) height4.29 in (109 mm) width5.67 in (144 mm) net weight15.87 oz (450 g) local signallingLED:power supplyLED:status GPRS)LED:communication Modbus)LED:communication Ethernet)LED:communication WiFi)LED:I/O Environment relative humidity5…95 % 131 °F (55 °C) without condensation IP degree of protectionIP20 terminal block)IP40 front face) ambient air temperature for operation-13…158 °F (-25…70 °C) ambient air temperature for storage-40…185 °F (-40…85 °C) pollution degree3 operating altitude6561.68 ft (2000 m) Ordering and shipping details Category09785 - POWERLOGIC SYSTEM CMPNTS Discount SchedulePL1 GTIN00785901433309 Package weight(Lbs)0.46 kg (1.02 lb(US)) ReturnabilityYes Country of originDE Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals which are known to the State of California to cause Carcinogen and Reproductive harm.For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins.
CatalogFormatSizeAdd to My DocumentsSize pdfSize 12.9 MBDate 9/17/19DescriptionNote that no printed catalogs are available but all necessary source files, in 14 sections, are available for download from the Shopping Kiosk.Size pdfSize 11.7 MBDate 4/2/19DescriptionThis catalog provides information on Enerlin'X including EIFE ethernet add-on module for MasterPact MTZ, smart system design, Enerlin'X components for smart systems, Com'X 210/510, FDM128 ethernet displays, FDM121 system displays, IFE system interface, EIFE embedded ethernet interface, Link150 ethernet gateway, commissioning software, and part number selection tables.User guideFormatSizeAdd to My DocumentsSize pdfSize 421.9 KBDate 1/1/17DescriptionThis guide provides an overview of the commissioning process for a new Com'X 510. These guidelines can help reduce commissioning time by eliminating unnecessary reboots and adding device configuration at the optimal time.Instruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages15
Software and FirmwareLanguage
Firmware - ReleasedFormatSizeAdd to My DocumentsSize zipSize 47.1 MBDate 9/18/19DescriptionCom’X v6.0.7 supports the following publication platforms:• Energy Operation• Digital Services Platform (DSP)• Comma Separated Values (CSV)Size zipSize 40 MBDate 1/29/16DescriptionCom’X firmware upgrade to address bug fixes.Updates:Com’X 200/210Known Issues:1. After upgrading to V2.1.18 from a previous version, the Com’X occasionally fails to communicate toconfigured Zigbee devices on its first startup. To correct this, cycle the power to the Com’X orpress “Restart” on the Maintenance > System Settings page. This is not a reoccurring issue.2. After upgrading to V2.1.18 from a previous version, measurements selected for publication arecleared. To continue to publish, the measurement selections must be reselected.Corrections:1. Corrected issue where after an upgrade to V2.1.17, the Local IDs defaulted to 1, causing loss ofcommunications to devices.2. Corrected issue where after an upgrade to V2.1.17, changing Local IDs in the Settings > ModbusGateway > Device IDs page caused the device to be removed or communications lost.Com’X 510Corrections:1. Corrected the issue of excessive time to load the Measurement Table for the CM4000 and CM3000variants, which also reduced the gateway bandwidth.2. Corrected issue where the data series in the 4 Weeks over 4 Weeks energy dashboard reportsinaccurate Date/Time values when the time zone is configured with a positive offset.3. Updated the on-board User Manual to the correct 2.1 version.
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.