View all FA, FH, FJ, FK, FY (F-frame) molded case circuit breakers and switches
FA/LA MOLDED CASE CIRCUIT BREAKER 480Y/277V 30A, 2P, 1PhShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
FAB14030A is replaced by:
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
- Reason for Substitution: End of life
- Substitution date: 13 June 2019
Main product or component typeCircuit breaker range of productI-Line Trip Unit TypeThermal-magnetic Rating CodeA Complementary Line Rated Current30 A Number of Poles1P Interrupt Rating10 kA 125 V DC14 kA 480 V AC18 kA 240 V AC [Ue] rated operational voltage277 V AC125 V DC mounting modeBolt-on electrical connectionI-Line connection lineBolted connection load Wire GaugeAWG 14...AWG 4 copper)1AWG 12...AWG 4 aluminium)1 Terminal TypeAL50FA magnetic hold current275 A magnetic tripping current600 A height162.56 mm (6.4 in) width38.10 mm (1.5 in) depth104.90 mm (4.13 in) Environment product certificationsUL listedCSA Ordering and shipping details Category01005 - FA 480V BREAKER & SWITCH Discount ScheduleDE2 GTIN00785901285205 Package weight(Lbs)1.14 kg (2.52 lb(US)) ReturnabilityNo Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP, which is known to the State of California to cause cancer, and DIDP, which is known to the State of California to cause Birth Defects or other reproductive harm.For more information go to www.p65warnings.ca.gov EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Environmental Disclosure Contractual warranty Warranty18 months
Instruction SheetFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages3
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.