View all PowerPact H-Frame Molded Case Circuit Breakers
Main product or component typeCircuit breaker range of productPowerPact H Trip Unit TypeThermal-magnetic breaking capacity codeD Complementary Line Rated Current125 A Number of Poles2P Interrupt Rating25 kA 240 V AC18 kA 480 V AC14 kA 600 V AC20 kA 250 V DC [Ue] rated operational voltage250 V DC600 V AC continuous current rating80 % mounting modeUnit mount electrical connectionBusbar connection lineBusbar connection load magnetic hold current900 A magnetic tripping current1700 A height162.56 mm (6.4 in) width69.60 mm (2.74 in) depth110.74 mm (4.36 in) tightening torque44.25 lbf.in (5 N.m) 0.00…0.15 in² (2.5…95 mm²) AWG 14...AWG 3/0) Environment product certificationsIECCCCUL listedCECSA ambient air temperature for operation104 °F (40 °C) Ordering and shipping details Category01110-HD,JD UNIT MT BREAKER/SWITCH Discount ScheduleDE2 GTIN00785901774679 ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsData BulletinFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.