View all PowerPact J-Frame Molded Case Circuit Breakers
Main product or component typeCircuit breaker range of productPowerPact J trip unit technologyThermal-magnetic breaking capacity codeD Complementary Line Rated Current200 A number of poles2 poles description2P breaking capacity25 kA 240 V AC18 kA 480 V AC14 kA 600 V AC20 kA 250 V DC [Ue] rated operational voltage600 V AC250 V DC continuous current rating80 % mounting modeI-Line electrical connectionI-Line connection lineLugs load AWG gaugeAWG 3/0...350 kcmil aluminium/copper phase connectionAC magnetic hold current1000 A magnetic tripping current2000 A height291.59 mm (11.48 in) width113.79 mm (4.48 in) depth149.10 mm (5.87 in) tightening torque230.12 lbf.in (26 N.m) 0.15…0.29 in² (95…185 mm²) AWG 3/0...350 kcmil) Environment product certificationsIECCCCCSAUL listedCE ambient air temperature for operation104 °F (40 °C) Ordering and shipping details Category01112 - HD, JD I-LINE BREAKER/SWITCH Discount ScheduleDE2 GTIN00785901912378 Package weight(Lbs)3.05 kg (6.72 lb(US)) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages10
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.