View all LA, LH, Q4 Molded Case Circuit Breakers
FA/LA MOLDED CASE CIRCUIT BREAKER, 600V, 400A, 3P, SHUNT TRIP, SHORT HANDLEShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker Trip Unit TypeThermal-magnetic OptionsShunt trip 120/208/240 V AC left side Complementary Line Rated Current400 A Number of Poles3P Interrupt Rating42 kA 240 V AC30 kA 480 V AC22 kA 600 V AC10 kA 125 V DC10 kA 250 V DC [Ue] rated operational voltage600 V AC250 V DC mounting modeUnit mount electrical connectionLugs loadLugs line Wire GaugeAWG 1...600 kcmil aluminium/copper)1AWG 1...250 kcmil aluminium/copper)2 Terminal TypeAL400LA magnetic hold current2000 A magnetic tripping current4000 A operator profileShort lever height279.40 mm (11 in) width152.40 mm (6 in) depth148.34 mm (5.84 in) tightening torque115.06 lbf.in (13 N.m) 0.07…0.47 in² (42…304 mm²) AWG 1...600 kcmil)115.06 lbf.in (13 N.m) 0.07…0.20 in² (42…127 mm²) AWG 1...250 kcmil) Environment product certificationsUL listedIECCSA Ordering and shipping details Category00935-LAL/LHL BRKR, SW, MAG-GARD Discount ScheduleDE2 GTIN00785901865131 Package weight(Lbs)16.48 lb(US) (7.475 kg) ReturnabilityNo Country of originMX Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen + Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Contractual warranty Warranty18 months
User guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction SheetSizeAdd to My DocumentsTripping curvesSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.