View all TeSys LRD Overload Relays
TeSys LRD thermal overload relays - 23...32 A - class 10AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeTeSys product nameTeSys LRD product or component typeNon differential thermal overload relay device short nameLR3D relay applicationMotor protection product compatibilityLC1D32LC1D25LC1D38 network typeDCAC thermal protection adjustment range23…32 A [Ui] rated insulation voltagePower circuit 600 V CSAPower circuit 600 V ULPower circuit 690 V IEC 60947-4-1 Complementary network frequency0...400 Hz mounting supportPlate, with specific accessoriesRail, with specific accessoriesUnder contactor tripping threshold1.14 +/- 0.06 Ir IEC 60947-4-1 [Ith] conventional free air thermal current5 A signalling circuit permissible current1.5 A 240 V AC-15 signalling circuit0.1 A 250 V DC-13 signalling circuit [Ue] rated operational voltage690 V AC 0...400 Hz [Uimp] rated impulse withstand voltage6 kV phase failure sensitivityTripping current 130 % of Ir on two phase, the last one at 0 control typeRed push-button stopBlue push-button reset temperature compensation-4…140 °F (-20…60 °C) connections - terminalsControl circuit screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²) flexible without cable endControl circuit screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²) flexible with cable endControl circuit screw clamp terminals 2 0.00…0.00 in² (1…2.5 mm²) solid without cable endPower circuit screw clamp terminals 1 0.00…0.02 in² (1.5…10 mm²) flexible without cable endPower circuit screw clamp terminals 1 0.00…0.01 in² (1…6 mm²) flexible with cable endPower circuit screw clamp terminals 1 0.00…0.02 in² (1.5…10 mm²) solid without cable end tightening torqueControl circuit 15.05 lbf.in (1.7 N.m) screw clamp terminalsPower circuit 22.13 lbf.in (2.5 N.m) screw clamp terminals width1.77 in (45 mm) depth2.76 in (70 mm) net weight0.27 lb(US) (0.124 kg) Environment protective treatmentTH IEC 60068 IP degree of protectionIP20 IEC 60529 ambient air temperature for operation-4…140 °F (-20…60 °C) without derating IEC 60947-4-1 ambient air temperature for storage-76…158 °F (-60…70 °C) flame retardanceV1 UL 94 mechanical robustnessVibrations6 Gn IEC 60068-2-6Shocks15 Gn for 11 ms IEC 60068-2-7 dielectric strength6 kV 50 Hz IEC 60255-5 standardsIEC 60947-4-1CSA C22.2 No 14EN 60947-4-1IEC 60947-5-1ATEX D 94/9/CEEN 60947-5-1UL 508 product certificationsRINABVLROS (Lloyds register of shipping)GLATEX INERISCCCULGOSTCSADNV Ordering and shipping details Category22347 - CONTACTOR,D-LINE,OVERLOADS-NEW Discount ScheduleI12 GTIN00785901234425 Package weight(Lbs)0.15 kg (0.32 lb(US)) ReturnabilityYes Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: Antimony oxide & Antimony trioxide which is known to the State of California to cause Carcinogen harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsSize pdfSize 6.5 MBDate 9/25/19DescriptionSection 16 of Digest 178 Catalog includes selection and ordering information for NEMA and definite purpose contactors and starters. Replaces Digest 177 section 16; 0100CT1501_SEC-16Data BulletinFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.