View all TeSys F Contactors
TeSys F - contactor coil - LX1FG - 42 V AC 50 HzShow more characteristics
LX1FG042LX1FG042 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeTeSys product or component typeContactor coil device short nameLX1FG range compatibilityTeSys F LC1F contactor product compatibilityLC1F185LC1F225 control circuit typeAC 50 Hz [Uc] control circuit voltage42 V AC 50 Hz average resistance0.57 Ohm 68 °F (20 °C) inductance of closed circuit0.09 H operating time20...35 ms closing7...15 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 131 °F (55 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsDrop-out 0.35...0.55 Uc 50/60 Hz 131 °F (55 °C))Operational 0.85...1.1 Uc 50/60 Hz 131 °F (55 °C)) inrush power in VA805 VA 50 Hz 0.3 68 °F (20 °C)) hold-in power consumption in VA55 VA 50 Hz 0.3 68 °F (20 °C)) heat dissipation18…24 W 50 Hz Environment ambient air temperature for operation23…131 °F (-5…55 °C) net weight1.21 lb(US) (0.55 kg) Ordering and shipping details Category22341-CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN03389110083217 Package weight(Lbs)1.19 lb(US) (0.540 kg) ReturnabilityNo Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.