View all TeSys F Contactors
TeSys F - contactor coil - LX4FG - 440...460 V DCShow more characteristics
LX4FG440 has not been replaced. Please contact your customer care center for more information.
Product availabilityNon-Stock - Not normally stocked in distribution facility
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product or component typeContactor coil device short nameLX4FG range compatibilityTeSys F LC1F contactor product compatibilityLC1F225LC1F185 control circuit typeDC low consumption [Uc] control circuit voltage440...460 V DC average resistance223 Ohm inrush 68 °F (20 °C)39700 Ohm holding 68 °F (20 °C) inductance of closed circuit4210 H operating time30...40 ms closing30...50 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 131 °F (55 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsOperational 0.85...1.1 Uc 131 °F (55 °C))Drop-out 0.15...0.2 Uc 131 °F (55 °C)) inrush power in W800 W 68 °F (20 °C)) hold-in power consumption in W5 W 68 °F (20 °C) Environment ambient air temperature for operation23…131 °F (-5…55 °C) net weight1.21 lb(US) (0.55 kg) Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN00785901247166 ReturnabilityNo Country of originCZ Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.