View all TeSys F Contactors
TeSys F - specific contactor coil - 440 V AC 40...400 Hz low consumptionShow more characteristics
LX9FJ937 has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product or component typeSpecific contactor coil device short nameLX9FJ range compatibilityTeSys F LC1F contactorTeSys F DR5TE rectifier product compatibilityDR5TELC1F400 control circuit typeAC 40...400 Hz low consumptionDC low consumption [Uc] control circuit voltage440 V AC 40...400 Hz440 V DC average resistance386 Ohm inrush 68 °F (20 °C)3690 Ohm holding 68 °F (20 °C) inductance of closed circuit19 H operating time60 ms opening50 ms closing mechanical durability10 Mcycles maximum operating rate3600 cyc/h 158 °F (70 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsOperational 0.85...1.1 Uc 131 °F (55 °C))Drop-out 0.3...0.5 Uc 131 °F (55 °C)) inrush power in VA500 VA 40...400 Hz 68 °F (20 °C)) hold-in power consumption in VA23 VA 40...400 Hz 68 °F (20 °C)) heat dissipation11.4…13.9 W Environment ambient air temperature for operation23…131 °F (-5…55 °C) net weight2.14 lb(US) (0.97 kg) Ordering and shipping details Category22341-CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN03389110248548 ReturnabilityNo Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.