View all TeSys D Contactors
TeSys D - contactor coil - LXD3 - 127 V AC 50/60 Hz for 40… 65 A contactorShow more characteristics
LXD3FC7 has not been replaced. Please contact your customer care center for more information.
Product availabilityNon-Stock - Not normally stocked in distribution facility
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product or component typeContactor coil device short nameLXD3 control circuit typeAC 50/60 Hz [Uc] control circuit voltage127 V AC 50/60 Hz average resistance60.29 Ohm 68 °F (20 °C) inductance of closed circuit3.34 H product compatibilityLC1D40A...D65ALC1DT80ALC1DT60A mechanical durability6 Mcycles maximum operating rate3600 cyc/h 140 °F (60 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsDrop-out 0.3...0.6 Uc 50/60 Hz 140 °F (60 °C))Operational 0.8...1.1 Uc 50 Hz 140 °F (60 °C))Operational 0.85...1.1 Uc 60 Hz 140 °F (60 °C)) inrush power in VA160 VA 60 Hz 0.75 68 °F (20 °C))160 VA 50 Hz 0.75 68 °F (20 °C)) hold-in power consumption in VA15 VA 60 Hz 0.3 68 °F (20 °C))15 VA 50 Hz 0.3 68 °F (20 °C)) heat dissipation4…5 W 50/60 Hz Environment ambient air temperature for operation23…140 °F (-5…60 °C) net weight0.15 lb(US) (0.07 kg) Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN03389119410380 ReturnabilityNo Country of originFR Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.