View all PowerLogic ION7400 series
PowerLogic ION7410 LV DC - Panel mount meter - display - optical port and 2 pulsShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main rangePowerLogic product namePowerLogic ION7400 device short nameION7410 product or component typePower meter Complementary power quality analysisEN 50160 2010 compliance reportIEEE 519 2014 compliance reportIEC 61000-4-30 class S power quality measurement up to the 63rd harmonic harmonic distortion waveform capture voltage sag and swell detection programmablity (logic and math functions)IEC 62586 power quality monitoringIEC 61000-4-15 flicker disturbance direction detection device applicationData aggregationRevenue billingWAGES meteringPower monitoring type of measurementCurrentVoltageFrequencyActive and reactive power totalApparent power totalPower factor totalActive and reactive power per phase, rmsApparent power per phase, rmsPower factor per phase, rmsActive and reactive energyApparent energy supply voltage20...60 V DC +/- 10 % network frequency50 Hz60 Hz Line Rated Current10 A1 A5 A poles description1P + N3P + N3P power consumption in W17 W display typeColour TFT LCD display resolution320 x 240 pixels QVGA sampling rate256 samples/cycle measurement current50…10000 mA analogue input typevoltage 5 MOhm) current 0.3 MOhm) measurement voltage57…400 V AC 42...69 Hz between phase and neutral100…690 V AC 42...69 Hz between phases frequency measurement range42…69 Hz number of inputs3 digital 30 V AC3 digital 60 V DC measurement accuracyCurrent +/- 0.1 %Voltage +/- 0.1 %Active energy +/- 0.2 % accuracy classClass 0.2S active energy IEC 62053-22Class 0.2 active energy ANSI C12.20Class 0.2 active power IEC 61557-12Class 0.5S reactive energy IEC 62053-24Class 0.5 power factor IEC 61557-12Class 0.2 voltage IEC 61557-12Class 0.2 current IEC 61557-12Class 0.2 frequency IEC 61557-12Class 0.2 active energy IEC 61557-12 number of outputs1 pulse information displayedVoltageCurrentFrequencyPowerEnergy consumptionHarmonic distortion communication port protocolModbus RTU 115 kbauds - 2-wireION 115 kbauds - 2-wireDNP3IEC 61850Modbus TCP/IPEthernet Modbus TCP/IP daisy chain 10/100 Mbit/sRSTP 801.1d 2004Ansi C12.19DLMS communication port supportEthernetScrew terminal block RS485Optical probe fiber opticMini B USB USB communication network typeIPv6 (internet protocol) data recordingData logsSag and swell logsWaveform logsTrending/forecastingSequence of event recordingGPS synchronisationHarmonics logsTime stampingAlarm logsEvent logsMin/max of instantaneous values memory capacity512 MB web servicesCustomizable home pageFile upload/download via FTPFile upload/download via SFTPWeb serverAlarm notification by e-mailViewing of captured waveform (FTP)Viewing of captured waveform (web)HTTPS server communication serviceSNMPSMTP e-mail notificationRSTP supportDHCPNTP time synchronizationPTP time synchronization cybersecurityEnable/disable communication portsPort hardeningSyslog protocol supportPassword protectionRobust security logs mounting modeFlush-mounted mounting supportFramework type of installationIndoor installation installation categoryIII Safety ConstructionIII, 400…690 V IEC 61010-1:ed. 3III, 400…690 V EN 61010-1:ed. 3III, 347…600 V UL 61010-1:ed. 3III, 347…600 V CSA C22.2 No 61010-1:ed. 3 standardsIEC 61557-12IEC 61326-1IEC 62052-11IEC 62053-24IEC 62053-22IEEE 1588IEC 62586 product certificationsCECULusN998China RoHS width3.86 in (98 mm) depth3.09 in (78.5 mm) height4.41 in (112 mm) net weight24.90 oz (706 g) Environment electromagnetic compatibilityElectrostatic discharge IEC 61000-4-2Radiated radio-frequency electromagnetic field immunity test IEC 61000-4-3Electrical fast transient/burst immunity test IEC 61000-4-4Surge immunity test IEC 61000-4-5Conducted RF disturbances IEC 61000-4-6Magnetic field at power frequency IEC 61000-4-8Voltage dips and interruptions immunity test IEC 61000-4-11Immunity to impulse waves IEC 61000-4-12Conducted and radiated emissions EN 55022Conducted and radiated emissions EN 55011Conducted and radiated emissions FCC Part 15Conducted and radiated emissions ICES-003Conducted RF disturbances 2...150 Hz) CLC/TR 50579Surge withstand IEEE C37.90.1 IP degree of protectionFront IP54 IEC 60529Body IP30 IEC 60529 relative humidity5…95 % ambient air temperature for operation-13…158 °F (-25…70 °C) ambient air temperature for storage-40…185 °F (-40…85 °C) operating altitude9842.52 ft (3000 m) Ordering and shipping details Category09793 - PLOGIC BRANCH CIRCUIT BCPM & MCM Discount SchedulePL1 Package weight(Lbs)3.63 kg (8 lb(US)) ReturnabilityNo Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: Dichloromethane (Methylene chloride) and Bisphenol A (BPA) which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins.
User guideFormatSizeAdd to My DocumentsSize pdfSize 95.2 KBDate 11/1/19DescriptionThis update provides a summary of technological advances in the Power and Energy Monitoring System offers, and the technical documentation accompanying their release.Size pdfSize 5.8 MBDate 11/1/19DescriptionThis document explains how to configure and operate ION7400 meters.Size pdfSize 947.6 KBDate 11/1/19DescriptionThis document describes the process to upgrade PowerLogic™ ION9000, PM8000 or ION7400 series meters to the latest firmware version. It also contains information about upgrading analog I/O option module firmware.Size pdfSize 112.4 KBDate 9/1/19DescriptionThis technical note outlines the compliance of applicable PowerLogic meters with the International Electrotechnical Commission’s IEC 61000-4-30 (or “4-30”) standard, and is intended for personnelwith knowledge of power quality and power quality standards.Size pdfSize 147.4 KBDate 7/1/19DescriptionThis protocol document provides setup instructions for using DLMS/COSEM withPowerLogic ION8650 (firmware v406 and later), ION7400 (firmware v1.4.1 andlater) and ION8800 (firmware v350 and later) meters.Size pdfSize 9.5 MBDate 10/26/18DescriptionOverview of ION architecture and details of all ION modulesInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages14
Software and FirmwareLanguage
Firmware - ReleasedFormatSizeAdd to My DocumentsSize zipSize 17.8 MBDate 11/20/19Files in documentzip16.7 MB942.2 KB161.9 KBDescriptionThis ZIP file contains the files to upgrade the PowerLogic™ ION7400 series meter to firmware v2.2.1 (V002.002.001), Meter Template, Modbus Map document, SNMP MIB, Webpages, What’s new document and other associated files. See the Upgrading Meter Firmware to v2.2.1 document for important information on performing this upgrade. Verify the checksum of the file to help ensure it was not corrupted during download using the SHA-256 File Signature for the ION9000_V002.002.001.zip file: 24d17cab3359d03cddc4ff3fdb0ee84b9a85022dfb24cb1ba9e30ecc6e4e5956. NOTE: To apply this firmware, the meter must have firmware v2.1.0. Go to schneider-electric.com and search for Upgrade devices to firmware v 2.1.0 and follow instructions on how to get and apply firmware v2.1.0.Size zipSize 16.8 MBDate 4/30/19Files in documentDescriptionFirmware version 2.1.0 for the PowerLogic™ ION7400 MID series meter adds enhanced firmware upgrade support, PTP, Secure HTTPS webserver, ION Module updates, updated support for the latest versions of EN50160, IEEE 519 and IEC 61000-4-30 power quality standards, pre- and post-event data capture for data and waveform recorders, and 0-20 mA support for the Analog I/O option module.To upgrade your meter to firmware version 2.1.0, you must use ION Setup version 3.1 or later. Please refer to the “Upgrading devices to firmware v2.1.0” technical note at https://www.se.com/ww/en/download/document/7EN72-0203/ for instructions on upgrading your meter firmware to version 2.1.0.SHA256 File signatures:f90c29967e1b94c3f4783c1524d03b01ed9418f0f71614bb65fec08848a1d224 *ION7400_MID_V002.001.000.zipSize s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmwarefor the METSEPM89M2600 Digital I/O Module is compatible with PM8000, ION7400, and ION9000 meters. SHA256 File signatures: 5f88067ed29ef9d7c369410fb1785967cf1838436062a0509c6aee1ad7f0c412 *METSEPM89M2600_DIO_V001.002.000_Release.s19Size s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmware for the METSEPM89M0024 Analog I/O Module adds 0-20 mA support when used with PM8000, ION7400, or ION9000 meter firmware 2.1.0 (V002.001.000) or higher. SHA256 File signatures: 77855de93e70ed9b25be9568b64eaa333c56ead286624323fbc04073cdb5626a *METSEPM89M0024_AIO_V001.002.000_Release.s19Size zipSize 28.6 MBDate 3/4/19Files in documentzip28.1 MB286 KB166.7 KBDescriptionFirmware version 2.1.0 for the PowerLogic™ ION7400 series meter adds enhanced firmware upgrade support, PTP, Secure HTTPS webserver, ION Module updates, updated support for the latest versions of EN50160, IEEE 519 and IEC 61000-4-30 power quality standards, pre- and post-event data capture for data and waveform recorders, and 0-20 mA support for the Analog I/O option module. To upgrade your meter to firmware version 2.1.0, you must use ION Setup version 3.1 or later. Please refer to the “Upgrading devices to firmware v2.1.0” technical note at https://www.se.com/ww/en/download/document/7EN72-0203/ for instructions on upgrading your meter firmware to version 2.1.0. SHA256 File signatures: 5f95a642a2c6401f38155e9984f3f1c11169ae9f0d8f6b9874246f180d205ba9 *ION7400_V002.001.000.zipSize zipSize 6.1 MBDate 2/21/19Files in documentbin5.8 MBDescription"Some RD96 displays may require a two-step firmware upgrade for compatibility with the ION9000 series meter. The RD96 display firmware must be upgraded with the rmdupg_rd96s_001.000.000_patch.bin file before proceeding with the standard rmdupg_rd96_004.000.000.bin display firmware upgrade file. See the ""RD96 Display upgrade using ION9000 meter.pdf"" document and the Power Meter user manual for additional information and display firmware upgrade instructions. Note: This remote display OS firmware is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older. SHA256 File signatures: 59c394c2c4f62cd2bb70ec2331b11ad0a03375818b83274c14ac6f8dc5644f82 *rmdupg_rd96s_001.000.000_patch.bin 83c30aca20c42622d99aced8f2981ec75de63021887750a6ba7e390aded68354 *RD96 Display upgrade using ION9000 meter.pdf"Size binSize 5.8 MBDate 10/16/18DescriptionThis is OS Package version 4.0.0 for the METSEPM89RD96 remote display. It supports meter firmware version 2.0.0, including the PowerLogic™ ION9000 series. See the Power Meter user manual for display firmware upgrade instructions. Note: This remote display OS Package is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older. SHA256 File signatures: 8b0aaa760d1e705b7528ee3941e381c00cab3adc524b460a9fd04acf54a0ef37 *rmdupg_rd96_004.000.000.binSize binSize 5.6 MBDate 10/16/18DescriptionThis is OS Package version 3.2.193 for the METSEPM89RD96 remote display. It supports PowerLogic™ PM8000 and ION74000 series meters with firmware versions 1.4.x and older. See the Power Meter user manual for display firmware upgrade instructions. Note: This remote display OS Package is not compatible with meters running firmware versions 2.0.0 and newer. SHA256 File signatures: c55b87fda044cc5def860129c460d87f6c57560868315f4454306c8a49efef67 *rmdupg_rd96.003.002.193.bin
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.