View all ClimaSys CR
ClimaSys PTC heating resistance 350-550W, 230V insulate thermoventilatorShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main rangeClimaSys product nameClimaSys CR product or component typeResistance heater with fan and thermostat power range400...550 W input voltage230 V AC 50/60 Hz electrical connection2 screw terminals 2.5 mm² Complementary operating positionVertical ambient air temperature for operation-40…158 °F (-40…70 °C) temperature setting range32…140 °F (0…60 °C) IP degree of protectionIP20 product certificationsULVDE height5.91 in (150 mm) width6.10 in (155 mm) depth8.46 in (215 mm) condition of useAir sealed enclosureHeaters must be installed with a thermal controllerElectrical protection is needed fixing modeBy clips mounting support35 mm DIN rail Ordering and shipping details Category80036 - ENCLOSURE SYSTEMS ACCESSORIES Discount ScheduleES1 GTIN00785901732662 Package weight(Lbs)1.03 kg (2.26 lb(US)) ReturnabilityYes Country of originDE Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals which are known to the State of California to cause Carcinogen & Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
CADSizeAdd to My DocumentsCAD Drawing Package for Thermal components (Version 1.0)CertificateSizeAdd to My Documents
Software and FirmwareLanguage
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.