Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range1000 A Line Rated Current1000 A breaking capacity100 kA 240 V AC65 kA 480 V AC25 kA 600 V AC AWG gaugeAWG 3/0...500 kcmil aluminium/copper)4 trip unit technologyElectronic, power, Micrologic 6.0 P, LSIG Complementary product certificationsIECCSAUL Listed [Ue] rated operational voltage600 V AC module typeP-Frame mounting locationBolt-on mounting modeUnit mount poles description3P breaking capacity codeJ electrical connectionLugs loadLugs line continuous current rating100 % device short nameA communication interfaceModbus Maximum Height16.16 in (410.46 mm) Maximum Depth8.05 in (204.47 mm) Maximum Width8.27 in (210.06 mm) tightening torque442.54 lbf.in (50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil)8.85…11.51 lbf.in (1.0…1.3 N.m) Ordering and shipping details Category01215-PG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 GTIN00785901974345 Package weight(Lbs)32.00 lb(US) (14.515 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 1.3 MBDate 5/12/20Files in documentChina RoHS declarationFormatSizeAdd to My DocumentsDimensions drawingFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages9
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.