Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range800 A Line Rated Current800 A breaking capacity65 kA 240 V AC50 kA 480 V AC50 kA 600 V AC AWG gaugeAWG 3/0...500 kcmil aluminium/copper)3 trip unit technologyElectronic, power, Micrologic 5.0 P, LSI Complementary product certificationsCSAUL ListedIEC [Ue] rated operational voltage600 V AC module typeP-Frame mounting locationBusbar mounting modeI-Line poles description3P breaking capacity codeK electrical connectionI-Line connection lineLugs load continuous current rating100 % device short nameA communication interfaceModbus Maximum Height12.86 in (326.64 mm) depth8.05 in (204.47 mm) width8.27 in (210.06 mm) tightening torque442.54 lbf.in (50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil)8.85…11.51 lbf.in (1.0…1.3 N.m) Ordering and shipping details Category01210-PG,H,J,K,L,N I-LINE BREAKERS Discount ScheduleDE2 Package weight(Lbs)32.00 lb(US) (14.515 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
CADFormatSizeAdd to My Documentsprp.document.label.format zipSize 1.3 MBDate 5/18/20China RoHS declarationFormatSizeAdd to My DocumentsDimensions drawingFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.