View all PowerPact P-Frame Molded Case Circuit Breakers
MOLDED CASE CIRCUIT BREAKER 600V 600AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range600 A Line Rated Current600 A breaking capacity65 kA 240 V AC50 kA 480 V AC50 kA 600 V AC AWG gaugeAWG 3/0...500 kcmil aluminium/copper)3 trip unit technologyElectronic, basic, ET 1.0I, LI Complementary product certificationsIECUL listedCSA [Ue] rated operational voltage600 V AC module typeP-Frame mounting locationBolt-on mounting modeUnit mount poles description3P breaking capacity codeK electrical connectionLugs loadLugs line continuous current rating80 % height326.64 mm (12.86 in) depth204.47 mm (8.05 in) width210.06 mm (8.27 in) tightening torque442.54 lbf.in (50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil)8.85…11.51 lbf.in (1.0…1.3 N.m) Ordering and shipping details Category01215-PG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 Package weight(Lbs)32.00 lb(US) (14.515 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.