View all I-Line Busway
Busway I-Line Circuit Breaker Plug-in Unit, 350A, M-Frame, 25kA-600V, 3W, HorizShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typePlug-in unit range of productI-Line circuit breaker typeM-frame trip unit technologyElectronic, basic, ET 1.0, LI Complementary protection typeCircuit breaker mounting modeBolt-on [Ue] rated operational voltage600 V AC Line Rated Current350 A Number of Phases3 phase poles description3P Interrupt Rating100 kA 240 V AC65 kA 480 V AC25 kA 600 V AC [Ics] rated service short-circuit breaking capacity80 % wiring configuration3-wire (integral ground bus) AWG gaugeAWG 3/0...500 kcmil 3 phase and neutralAWG 6...300 kcmil 4 ground depth24.84 in (631 mm) height24.21 in (615 mm) width50.20 in (1275 mm) condition of useHorizontal installation Environment product certificationsUL listed file E22182CSA C22.2 No 27 standardsUL 857 Ordering and shipping details Category20192-PBMH/PTMH C/B PLUGS Discount SchedulePE7 Package weight(Lbs)284.00 lb(US) (128.820 kg) ReturnabilityNo Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Nickel compounds and Di-isodecyl phthalate (DIDP) which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
Instruction SheetFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsTripping curvesFormatSizeAdd to My DocumentsSize pdfSize 181.9 KBDate 1/30/08DescriptionTime current curve 613-14 for ET 1.0 0613TC0814 48095-0613-14
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.