View all PowerPact Q-Frame Molded Case Circuit Breakers
PowerPact Q - molded case circuit breaker - 3-pole - 10 kA - 208Y/120 V - 125 AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic Complementary Line Rated Current125 A [Ue] rated operational voltage208Y/120 V AC number of poles3 breaking capacity10 kA 240 V AC continuous current rating80 % breaking capacity codeB mounting modeUnit mount electrical connectionLugs loadTerminal nut line AWG 4...300 kcmil aluminium/copper magnetic hold current1200 A magnetic tripping current2400 A height164.34 mm (6.47 in) width114.30 mm (4.5 in) depth99.82 mm (3.93 in) tightening torque247.82 lbf.in (28 N.m) 0.04…0.23 in² (25…150 mm²) AWG 4...300 kcmil) Environment product certificationsIECCSAUL listed Ordering and shipping details Category00187-Q2M REPL MAIN CB Discount ScheduleDE2A GTIN00785901704010 Package weight(Lbs)4.53 lb(US) (2.055 kg) ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.