View all PowerPact Q-Frame Molded Case Circuit Breakers
PowerPact Q - molded case circuit breaker - 3-pole - 25 kA - 240 V - 90 AShow more characteristics
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic Complementary Line Rated Current90 A [Ue] rated operational voltage240 V AC number of poles3 breaking capacity25 kA 240 V AC continuous current rating80 % breaking capacity codeD mounting modeUnit mount electrical connectionLugs load AWG 4...300 kcmil aluminium/copperLugs line AWG 4...300 kcmil aluminium/copper magnetic hold current1000 A magnetic tripping current1800 A height6.47 in (164.34 mm) width4.5 in (114.30 mm) depth3.93 in (99.82 mm) tightening torque247.82 lbf.in (28 N.m) 0.04…0.23 in² (25…150 mm²) AWG 4...300 kcmil) Environment product certificationsIECUL ListedCSA Ordering and shipping details Category00005 - QO,Q2L 2P ENCL & BREAKERS Discount ScheduleDE2A GTIN00785901522874 ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages13
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.