View all QO™ Load Centers
Load Center, QO, Qwik Grip, Main Lug, Plug On Neutral, 24SP, 125A, NEMA1 W/GNDShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main ProductLoad Center Marketing Trade NameQO Complementary Load Center TypeMain lugs Line Rated Current125 A number of spaces24 Short Circuit Current Rating65 kA Maximum Number of Single Pole Circuits24 Maximum Number of Tandem Breakers0 Number of Phases1 phase Voltage Rating120/240 V AC Wire SizeAWG 6...AWG 2/0 aluminium/copper Grounding BarGrounding bar (factory installed) Busbar MaterialCopper busbar Enclosure MaterialWelded sheet steel Cover FinishBaked enamel grey box number7Q height20.91 in (531 mm) width14.25 in (362 mm) depth3.74 in (95 mm) tightening torque5.65 N.m (50 lbf.in) AWG 6...AWG 2/0) Environment Enclosure RatingNEMA 1 indoor ambient air temperature for operation23 °F (-5 °C)104 °F (40 °C) product certificationsUL listed Ordering and shipping details Category10003 - QO PON 1PH LC,12-60 CKT, ML N1 Discount ScheduleDE3A GTIN00785901607397 Package weight(Lbs)5.80 kg (12.79 lb(US)) ReturnabilityYes Country of originUS Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause Carcinogen & Reproductive harm. For more information go to www.p65warnings.ca.gov EU RoHS DirectiveUnder investigation
CatalogFormatSizeAdd to My DocumentsSize pdfSize 3 MBDate 9/13/19DescriptionDigest 178 catalog section 1 - This section of Digest 178 provides selection information for QO™ and Homeline™ Miniature Circuit Breakers (MCBs), QO and Homeline load centers, CSEDs, Surge Protective Devices (SPDs), and Servicepak™ power outlets. Replaces Digest 177 section 1; 0100CT1501_SEC-01CADFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsSize pdfSize 1.7 MBDate 2/1/14DescriptionThis bulletin contains instructions for the installation and operation of QO and Homeline load centers. It also includes installation instructions for standard and tandem branch circuit breakers. See separate instructionbulletins included with advanced function circuit breakers and accessories, when installed.EU RoHS DeclarationFormatSizeAdd to My DocumentsHandoutFormatSizeAdd to My DocumentsSize pdfSize 604.5 KBDate 7/20/18DescriptionElectrical contractors will appreciate not having to remove knockouts, install wire connectors and blindly pull wire into the load center versus the ability to slide wires from the front with the Qwik-Grip wire management system. A quick bend of the wire using the wire bend guide on the Qwik-Grip insert and the wire easily slides into the slot. Once done, snap on the Qwik-Grip shield to keep the wires behind the router for a secure, code compliant installation. Qwik-Grip, a state of the art wire management system, allowing you to move on the next job quicker.
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.