View all PowerPact R-Frame Molded Case Circuit Breakers
MOLDED CASE CIRCUIT BREAKER 600V 2000AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact R current sensor rating range2000 A trip unit technologyElectronic, basic, ET 1.0I, LI Complementary [Ie] rated operational current2000 A [Ue] rated operational voltage600 V AC mounting modeUnit mount poles description2P breaking capacity65 kA 240 V AC35 kA 480 V AC18 kA 600 V AC breaking capacity codeG continuous current rating80 % electrical connectionBusbar connection lineBusbar connection load height412.50 mm (16.24 in) width419.86 mm (16.53 in) depth368.05 mm (14.49 in) tightening torque601.85 lbf.in (68 N.m) 0.08…0.62 in² (50…400 mm²) AWG 1/0...750 kcmil)601.85 lbf.in (68 N.m) 0.08…0.23 in² (50…150 mm²) AWG 1/0...300 kcmil) Environment product certificationsIECUL listedCSA Ordering and shipping details Category01245-RG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 Package weight(Lbs)74.00 lb(US) (33.566 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.