Main product or component typeCircuit breaker range of productPowerPact R current sensor rating range1600 A trip unit technologyElectronic, ammeter, Micrologic 6.0 A, LSIG Complementary [Ie] rated operational current1600 A [Ue] rated operational voltage600 V AC mounting modeUnit mount poles description3P breaking capacity125 kA 240 V AC100 kA 480 V AC50 kA 600 V AC breaking capacity codeL continuous current rating100 % electrical connectionBusbar connection lineBusbar connection load Maximum Height16.24 in (412.50 mm) Maximum Width16.53 in (419.86 mm) Maximum Depth14.49 in (368.05 mm) tightening torque601.85 lbf.in (68 N.m) 0.08…0.62 in² (50…400 mm²) AWG 1/0...750 kcmil)601.85 lbf.in (68 N.m) 0.08…0.23 in² (50…150 mm²) AWG 1/0...300 kcmil) Environment product certificationsCSAIECUL Listed Ordering and shipping details Category01245-RG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 GTIN00785901234036 Package weight(Lbs)52.00 lb(US) (23.587 kg) ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Data BulletinFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 2.5 MBDate 5/18/20CertificateFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDimensions drawingFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages26
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.